The most obvious cause for a low coolant level is either an external or internal leak. While many
generators are equipped with this alarm, few generators have a dedicated alarm indicator for low coolant.
Usually, this alarm will be tied into a high coolant temp shutdown. If the generator is equipped with an “Approaching High Coolant Temp Alarm” or “High Coolant Temp Pre Alarm,” you can determine which fault caused the shutdown.
The block heater actually heats the coolant which circulates around the
engine block. Keeping the engine block warm prevents the oil from becoming too thick in cold temperatures.
A common misconception is that the engine does not need a block heater in warm climates. A block heater does more than help the engine to start in cold weather. Due to the dissimilar metals that the engines are built with, accelerated wear can occur during start up. The pistons, normally made of aluminum, will expand at a faster rate than the iron cylinder liners. This rapid expansion of the pistons can lead to scuffing of the piston skirt.
Block heaters relieve most of this scuffing by maintaining the cooling system temperature and keeping the cylinder liners expanded.
Low Coolant Temp Alarms are mainly the result of faulty block heaters. These heaters run 24 hours a
day, 7 days a week, and periodically, they are going to fail. A block heater, however, will never cause the engine not to run. The
extreme temperature inside the block heater is what causes the coolant to circulate through the system. At times you can hear the
coolant boiling inside the block heater.
Leaks can be prevented by performing routine
Most often oil leaks are not, in fact, leaks, but the result of “wet stacking” (or “engine slobber”).
Wet stacking is the accumulation of carbon particles, un-burned fuel, lube oil, condensed water and acids in the exhaust system.
The most common coolant leak occurs in the block heater hoses. Due to the extreme temperatures produced by the block heaters it causes the heater hoses to fatigue more quickly.
The most common fuel leak service calls are due to overfilling of the base tank. This is typically caused by human error or a failure of a pump system. In order to prevent this from occurring it is always recommended that you have a trained professional fuel your generator.
Generators have a control or “enunciation” panel. This panel controls all aspects of the
settings, running of and shutdown of the generator. It displays all critical engine and alternator information and displays any
“faults” that have caused it to shut down the generator. 99% of service calls received for generator controls “Not In
Auto” are the direct result of human error.
The obvious reason for not in auto is the main control switch has been put into the “Off/Reset” position. The control switch may have several positions, as in “Off/Reset” and “Cool Down”, which will cause the generator not to start in the event of a power outage. These positions should give an alarm.“Not In Auto” is a generic term for the unit not being shut off and may not actually be the main control switch.
Alarms not reset, breakers open, switch gear not reset and emergency stop buttons activated are all examples of not in auto failures. Several generators are set up to short trip the main circuit breaker during an emergency fault shutdown. When the generator shuts itself down (for any reason), someone has to physically reset the control panel to clear the alarm.
This is a common problem with newer generators that are not exercised on a regular basis. Closer tolerances
within the fuel systems to meet today’s emission requirements make fuel systems more susceptible to air affecting the ability of the
generator to start up. This is not as common with older generators. Older generators that experience this problem may have a leak in a
line or check valves that are not properly holding the fuel in the engine.
fuel level gauges may not always be accurate. Unlike a vehicle that is moving and using a higher percentage of its tank’s
capacity, a generator tank has no movement, causing the fuel to become stagnant. Mechanical gauges may also stick in a position until
vibrations break them free. Some generators are equipped with “Low Fuel Level Shutdown” or “Critical Fuel Level
Shutdown”. The control panel will shut the generator down to prevent the fuel system from taking in air, when fuel depletion is
fuel level alarms are required by government regulations to prevent the overfilling of a fuel tank. The alarm should activate when
the fuel tank reaches between 90%-95% capacity. This lets the person fueling the tank know when they should stop filling. There
is normally nothing wrong with the generator when this alarm activates.
On rare occasions, the natural thermal expansion of the fuel will cause the alarm to activate. This will usually occur on an extremely hot summer day. High fuel level alarms may or may not clear themselves when the fuel level drops below the set point. You may have to manually reset the alarm when the fuel level drops.
service call will usually come in as “We are in a power
and the generator doesn’t start”. First, verify that nobody has accidentally pushed a remote “Emergency Power-Off
The status of the automatic transfer switch should be checked during a power outage. The ATS should have some kind of lights or display showing the switch position and source availability. Never try to manually operate an automatic transfer switch, if you do not know how to do so properly. Severe bodily injury or immediate death can occur.
The transfer switch is smarter than you may think and has a specific reason for being in the position that it is in: Attempting manual operation may drag you into a live bus if it is done incorrectly.
After a local power outage, many service calls come in stating that “utility power is back on and the
generator is still on.” There are a couple of reasons for this. One reason is a timer delay in the automatic transfer
switch that will keep the generator online until the automatic transfer switch sees a steady supply of clean power coming from the utility
grid. This timer is usually set between 15 and 30 minutes.
Any glitch in power within that time will restart the timer. Another reason the generator will stay online is the In Phase Monitor. The automatic transfer switch may be set to have the phase angle of the generator match the phase angle of the utility grid prior to re-transfer.
Power Plus! is a leading provider of reliable non-radioactive power generators across the United States and Canada.
Have a question or comment for Power Plus!? We'd love to hear from you!
Please provide your contact information and we'll get back to you as soon as we can.
Contact Power Plus @ (800) 863-2525 | email@example.com